- Checked for faults: no codes stored. Checked hall sensor and microswitch values: OK. Checked power to pump: none present. Found permanent fuse in power distribution block blown. Found dead short in hydraulic pump. Replaced power block and pump. FIlled and bled system. Top operating correctly at this time.
- Install customer supplied door panel
- Perform report card as recommended by Manufacturer.
- VIRGINIA STATE INSPECTION
- Sublet to have both door panels repaired
Maryann J. gave our service a 5 star review on 1/21/2021